UDGEfficient, intuituve and stylish
Programmable Thermostats with built-in GFCI
An “all-in-one” programmable thermostats for electric underfloor heating control where optimal comfort temperature and minimum energy consumption is required.
EFFICIENT, INTUITIVE AND STYLISH
- Simple user interface and thoughtful installation design
- Pre-programmed for quick set-up
- Monitored energy consumption
- Simple operation – no need for manual
- Multi voltage: 120 – 240 V (incl. 208 V)
- Output relay: 15 A
- Large back-lit display for easy reading
- Single thermostat for all applications (room, floor, room with floor limititation and as regulator)
- Industrial Design:
USA – Design Patent No. D768092
Canada – Design Patent No. 161353
|Product Sheet, UDG / USG, English|
File type/size:PDF ( 587.86 KB )
|User Manual, UCG / UDG (EN-US, FR-CA, ES-MX)|
File type/size:PDF ( 6.89 MB )
|Quick GUide, UDG / ADG (EN-US, FR-CA, EX-MX)|
File type/size:PDF ( 703.42 KB )
|Instructions, UDG / UCG / UTN / USG (EN-US, FR-CA, ES-MX)|
File type/size:PDF ( 368.92 KB )
The program settings are permanent, the clock will be reset after 2 to 4 hours.
- From the home screen
- Press "OK" button twice
- Press button UP and DOWN simultaneously for 3 sec.
- Unlock Child Lock (video)
Error code "E2" means defective, damaged or not connected floor sensor. Check connections or replace sensor if necessary.
Your heat mat or installation between thermostat and heat mat has a fault current to ground. The thermostat has cut off the power for your safety. Please contact your local electrician.
Check the connections between the two units. If the USG is connected incorrectly to the thermostat, the USG won't switch off.
The ground wire in the floor mat must be connected directly to the ground wire of the supply.
The recommended night setback is max 5°C/41°F
Yes the adaptive function is reset during a factory reset.
What is the maximum length of the sensor cable?
In general, it is recommended that the maximum sensor cable length should be 164 feet/50 meters, the length might be shorter. Read the instructions for the precise maximum length.
"E2" means defective, damaged or disconnected floor sensor. Sensor resistance should be 10 or 12 kOhm at 25°C (77°F). The onstruction or quick guide holds informatiom for the specific thermostats.
We deliver high-quality product platforms as the perfect foundation for your customisation and differentiation. Having unique, customised solutions enables you to set yourself apart in the market on the exact parameters that are important to you and your customers.