ETVVersions with floor sensor or remote room sensor
OJ DIN Rail Thermostats – with setback mode for control of electrical heating. The ETV is suitable when remote control of the system is required. It is a compact thermostat saving space on the panel. ETV has setback temperature function, which is activated via external timer. Setback temperature is fixed 5ºC.
- Suitable when remote control of the system is required
- Setback temperature function, activated via external timer
- Compact and space-saving
|Product Sheet, ETV, English
File type/size:PDF ( 460,82 kB )
|Product Sheet, ETV, Finnish
File type/size:PDF ( 202,21 kB )
|Product Sheet, ETV, German
File type/size:PDF ( 212,60 kB )
|Product Sheet, ETV, Russian
File type/size:PDF ( 263,74 kB )
|Product Catalogue 2023 Europe-Asia-South-America, English
File type/size:PDF ( 2,59 MB )
|Product Catalogue 2023, Australasia / Africa, English
File type/size:PDF ( 4,00 MB )
|Instructions, ETV (DA, NO, SV, FI, EN, DE, PL, RU, FR, ZH)
File type/size:PDF ( 252,44 kB )
|Instructions, ETV (EN, DE)
File type/size:PDF ( 81,91 kB )
What is the maximum length of the sensor cable?
In general, it is recommended that the maximum sensor cable length should be 164 feet/50 meters, the length might be shorter. Read the instructions for the precise maximum length.
"E2" means defective, damaged or disconnected floor sensor. Sensor resistance should be 10 or 12 kOhm at 25°C (77°F). The onstruction or quick guide holds informatiom for the specific thermostats.
The ground wire in the floor mat must be connected directly to the ground wire of the supply.
The recommended night setback is max 5°C/41°F
Yes the adaptive function is reset during a factory reset.
We deliver high-quality product platforms as the perfect foundation for your customisation and differentiation. Having unique, customised solutions enables you to set yourself apart in the market on the exact parameters that are important to you and your customers.