OCD24-event clock thermostat incl. 2 sensors
4-Event OJ Microline® Clock Thermostat OCD2
OCD2 has built-in clock function and is provided 4-event program for automatic temperature control. The thermostat has adaptive function meaning the thermostat calculates when the heating has to be switched on to make sure that the comfort temperature is obtained at the required time. All settings and the clock are maintained if the thermostat is switched off by the built-in interrupter.
- Min. temperature limitation: For better heating comfort
- Max. temperature limitation: Protection of i.e. wooden floors
- 4-event Clock thermostat with 2 sensors
- Built in room sensor and floor sensor
|Product Sheet, OCD2-1999, English
File type/size:PDF ( 824.40 KB )
|Product Sheet, OCD2-1999, German
File type/size:PDF ( 474.08 KB )
|Product Sheet, OCD2-1999, Russian
File type/size:PDF ( 481.17 KB )
|Product Catalogue 2021 Europe-Asia-South-America, English
File type/size:PDF ( 2.65 MB )
|User Manual, OCD2 (EN, DE, RU, PL, UK)
File type/size:PDF ( 620.87 KB )
|Instructions, OCD2 (EN, DE, RU, PL, NL, FR, SV, DA, UK)
File type/size:PDF ( 234.60 KB )
Press both UP and DOWN buttons together for 3 seconds. INFO is displayed.
Press UP button until you reach the "APP" sub menu. Select the sub menu with the OK button.
Try changing application type. If "roLi" is available the thermostat is a OCD2
We have a OCC2 for under floor bathroom heating. The thermostat / clock keeps clicking on and off every few seconds, when it is supposed to be heating up. The display goes blank and then reappears with an audible click for a few seconds. What is happening?
The internal power supply of the thermostat has over the years deteriorated. Please contact your local dealer for replacement.
The backup time on the OCC2/OCD2 is 48 hours.
Error code "E2" means defective, damaged or not connected floor sensor. Check connections or replace sensor if necessary.
The recommended night setback is max 5°C/41°F
Yes the adaptive function is reset during a factory reset.
The ground wire in the floor mat must be connected directly to the ground wire of the supply.
In general, it is recommended that the maximum sensor cable length should be 164 feet/50 meters, the length might be shorter. Read the instructions for the precise maximum length.
"E2" means defective, damaged or disconnected floor sensor. Sensor resistance should be 10 or 12 kOhm at 25°C (77°F). The onstruction or quick guide holds informatiom for the specific thermostats.
We deliver high-quality product platforms as the perfect foundation for your customisation and differentiation. Having unique, customised solutions enables you to set yourself apart in the market on the exact parameters that are important to you and your customers.